i would say you need 2 circuits, one for the outlets and another for the lights.
Now, that is easiest I have seen that explained! Thanks for that!:thumbsup:If there is only one outgoing cable from the switch box for 2 separately switched fixture you would use xx-3 cable. Black is one fixture, red is the other.
That's what I thought. Thanks for all your help!You could use two xx-2 cables with one to each fixture. Box fill will be more crowded in the switch box.