So I ripped out the old lights and now I have the two wires that were running to them all. From my tests one wire has constant power and one line never has power so I'm assuming(and from tracing) that the one that never has power is connected to the three way switches. I'm replacing the lights that were up there with recessed lights so I need a way to wire them correctly but I can't seem to wrap my head around the three way end of line deal. I'm pretty sure this is how it works(see image).
22.6 KB Views: 930