Discussion Starter · #1 ·
I am adding some new under cabinet lighting and wiring it into an existing single pole light switch and wall outlet. Ahead of this is a GFCI outlet. Whenever I add the wiring, it trips the GFCI outlet. Can someone tell me what I am doing incorrect please?