Discussion Starter · #1 ·
I have a rewire question...I want to bring hot to box#1 which will power a 3 way switch for a living room split receptacle for a floor lamp. I will have 14/3 going from box #1 to the other side of the living room to box #2 which will have the other 3 way to control a split receptacle. I also have a fan switch in box #2. Can I power the fan switch off 3 way in that same box that is switching the receptacle. After the 2nd 3 way is that where I take 14/2 down to wire the split receptacle? I hope that is not too confusing..or is there and easier way?