Discussion Starter · #1 ·
I'm installing an oven in a remodeled kitchen and just noticed that although the 2 hot wires are 6 gauge there is no neutral and the ground is bare and only what looks like 10 gauge. Is this a problem? I know the loads are balanced but do I need to pull a new cable or a separate bigger neutral/ground? Thanks for the help!