Discussion Starter · #1 ·
using 10/2 with ground for compressor. At the panel and disconnect switch I marked the white wire with red tape. I marked it red because of the black, red and white wires in a 10/3 (red being one of two hots). All comments I've seen discuss marking a hot white with black. Should I change the marking from red to black?