I think any notch is a really bad idea, especially if it's in the bottom of a joist, and in the middle of the span. Definitely would not do it, code or not.
I agree. I don't mind drilling holes, but notching seems like it could cause the joists to lose a lot of integrity. Maybe that's just me being OCD...Red Squirrel said:I think any notch is a really bad idea, especially if it's in the bottom of a joist, and in the middle of the span. Definitely would not do it, code or not.
You need the pic to see what they are talking about.......and a bored hole is the same as a drilled hole.....I'm missing it.
"R502.8 Drilling and notching.Structural floor members shall not be cut, bored or notched in excess of the limitations specified in this section. See Figure R502.8.
R502.8.1 Sawn lumber.Notches in solid lumber joists, rafters and beams shall not exceed one-sixth of the depth of the member, shall not be longer than one-third of the depth of the member and shall not be located in the middle one-third of the span. Notches at the ends of the member shall not exceed one-fourth the depth of the member. The tension side of members 4 inches (102 mm) or greater in nominal thickness shall not be notched except at the ends of the members. The diameter of holes bored or cut into members shall not exceed one-third the depth of the member. Holes shall not be closer than 2 inches (51 mm) to the top or bottom of the member, or to any other hole located in the member. Where the member is also notched, the hole shall not be closer than 2 inches (51 mm) to the notch."
Is it in this, or somewhere else?
Sure, a hole is a hole; but its not a notch.You need the pic to see what they are talking about.......and a bored hole is the same as a drilled hole.....
No holes are notches in the middle 3rd.
We are not saying they are the same, you can't have notches or holes in the middle third.Sure, a hole is a hole; but its not a notch.
It says no notches in the center third. But it doesn't prohibit holes.
But maybe I am confused. In electrical talk is a notch the same as a hole? Normally a notch is removing material from the top or bottom, while a hole is removing material from the middle while not disturbing the top or bottom. But you guys seem to be saying they are the same.
I think you could be correct, Im pretty sure Connecticut treats a hole as a notch and disallows any drilling in the middle third, but in any case, there seems to be a lot of debate on whether or not a bored hole is to be treated as a notch.Where does it say that? The reference ONLY states no notches in the middle third. It does not state no holes in the middle third.
THANK YOU!Where does it say that? The reference ONLY states no notches in the middle third. It does not state no holes in the middle third.
I was taught it was never allowed, just one of those things, that's why it's so important to self educate yourself in actual codes, not by what your co-worker or employer says... we all fall victim of this at some point in our lives, glad I learned something myself... i've looked at that IRC section before too, I just read what I wanted it to say. Or believed what it should say.I couldn't imagine why they would care about holes in the middle third.