For NEW construction and larger remodeling projects.Hello all, I've been learning a lot just reading through over the last month or so. I see that under NEC 2011 a neutral is required in switch boxes.
You probably don't need to do more.Since I'm replacing some wiring in a basement bathroom
...and you're done.The wiring comes from the panel to a can light which will be switched. From there a plan on 14/2 to the switch box...