I just converted a 125 amp GE panel from a main panel to a sub-panel. It is now connected (thru PVC conduit) to a 60 amp breaker in the main Square D panel in a detached building.
I separated the neutrals and grounds and only the grounds are bonded to the can.
It was much easier to add 3 ground bars in different areas of the panel than to pig-tail onto the ground leads and then all land on 1 ground bar.
This is an older thread, you may not receive a response, and could
be reviving an old thread. Please consider creating a new thread.
DIY Home Improvement Forum
A forum community dedicated to Do it yourself-ers and home improvement enthusiasts. Come join the discussion about tools, projects, builds, styles, scales, reviews, accessories, classifieds, and more! Helping You to Do It Yourself!