1 - 12 of 12 Posts

#### Troy32

· Registered
Joined
·
294 Posts
Discussion Starter · ·
I am building a wood shop in my basement and need to run a series of outlets. I am using 12/2 and a 20 amp circuit. I have a 50 foot run to where i want the first outlet. I would then need to go another 40 feet around portion of the basement and back to where the wire came from to connect all of the outlets. Would I be better off splicing the wire at the 50 foot mark and running 2 20 foot sections to reduce the length or just run on continuous length?

Thanks,
Troy

#### Dave632

· Registered
Joined
·
203 Posts
I am building a wood shop in my basement and need to run a series of outlets. I am using 12/2 and a 20 amp circuit. I have a 50 foot run to where i want the first outlet. I would then need to go another 40 feet around portion of the basement and back to where the wire came from to connect all of the outlets. Would I be better off splicing the wire at the 50 foot mark and running 2 20 foot sections to reduce the length or just run on continuous length?

Thanks,
Troy
The fewer splices you make, the fewer places for a connection to come loose.

#### Troy32

· Registered
Joined
·
294 Posts
Discussion Starter · ·
Exactly. I like to make as few connections as possible but also did not want a 90ft run on a circuit that will have high amp draw machines

#### rjniles

· A "Handy Husband"
Joined
·
15,049 Posts
Are you saying the last receptacle is nearer the breaker box than the first receptacle? I can't picture your layout. Can you post a diagram.

#### Bondo

· Master General ReEngineer
Joined
·
10,523 Posts
Are you saying the last receptacle is nearer the breaker box than the first receptacle? I can't picture your layout. Can you post a diagram.
Ayuh,.... Sounds like just callin' the last outlet, the 1st, insteada wirin' a loop around the shop, would work...

Come outa the box, to the gang of outlets, 'n then continue on to the last outlet...

#### Dave632

· Registered
Joined
·
203 Posts
You can "T" in an outlet or junction box to shorten the total length of run.

90 ft with 12/2 wiring will have minimal voltage drop.

#### k_buz

· Licensed Electrician
Joined
·
4,352 Posts
The only reason I would choose to make that run shorter would be to decrease the cost of the installation.

#### Troy32

· Registered
Joined
·
294 Posts
Discussion Starter · ·
Imagine a question mark and the box would be by the bottom of the question mark. The outlets will go all the way around 3 walls. I already have plenty of wire so cost does not play a factor. Either way will work but I was curious which way a professional would run it.

Thanks for the info so far

#### Jim Port

· Super Moderator
Joined
·
18,303 Posts
Run the wiring however makes the most sense and uses the shortest amount of wire. There is no reason to backtrack.

NJMarine

#### Troy32

· Registered
Joined
·
294 Posts
Discussion Starter · ·
That was the question. What makes the most sense?

#### diystephen

· Engineer
Joined
·
191 Posts
Exactly. I like to make as few connections as possible but also did not want a 90ft run on a circuit that will have high amp draw machines
I think to get the correct advice on this project you'll need to post some more detail. Above you list "high amp draw machines." What exactly are you planning to run of the 20A circuit? It's entirely possible that you'll need more than 1 circuit, so that could impact the wiring layout.

#### Troy32

· Registered
Joined
·
294 Posts
Discussion Starter · ·
I will be using up to 15 amp tools but never more then one at a time. One circuit should be fine

1 - 12 of 12 Posts
This is an older thread, you may not receive a response, and could be reviving an old thread. Please consider creating a new thread.