there is a few regular outlets in the garage.
The compressor is a 60gal 3.7hp not sure if it will work on 120V
the laundry is right next to the garage tho just a wall separating it, would i be able to run another outlet from the dryer into the garage?
You can't run an extension cord thru a wall. Nor are you to use them in place of permanent wiring.
You need to run a new circuit to the garage for the compressor.
If you anticipate future electrical growth in the garage, whether 120V or240V, I would consider running a feeder (larger than what you would run for the compressor) to a subpanel in the garage, then a circuit from the sub to compressor.
Oso954's idea is the best so far.
By do it that way you would have enough amps to run even more machinery, add a 220 volt window A/C, run the lights on one circuit, outlets on another and not have the lights dimming and having to run inside the house if a breaker trips.
All the outlet wiring should have been on it's own ciruuit on a 20 amp breaker and be 12-2, with GFI protection.
1 - 8 of 8 Posts
This is an older thread, you may not receive a response, and could be reviving an old thread. Please consider creating a new thread.
A forum community dedicated to Do it yourself-ers and home improvement enthusiasts. Come join the discussion about tools, projects, builds, styles, scales, reviews, accessories, classifieds, and more! Helping You to Do It Yourself!