No. 90 amps only. You're getting your information from the wrong chart or sources. Look it up for yourself, it's on table 310.15(B)(16) aluminum section 75C column.Southwire (By-the-Foot) 2-2-2-4 Gray Stranded AL SER Cable-13102999 - The Home Depot
This would would fit my bracker box and be good for 100 amps right?
Nope. All due respect, you've been misled by wire salesmen.1/0 for 3% 100 amp.