Last night I finally tracked down where the cable that goes outside to my lamp post runs... It's on our basement lighting circuit, and runs from the service panel all the way across the house (about 60 ft) as NM 14/2 cable then goes into a junction box (which had no cover on it, what a supprise there) in the drop ceiling of the basement then turns into 2 conductor (I dont think it has a ground wire UF cable then that runs to the wall facing the pole and what appears to be out through the concrete block! is this even allowed? Should it of been done another way? I am going to replace the pole this spring, but wanted to make sure the line was fine before I got to that point... thanks!