i am praying for advice
You need to be patient. Alot of folks are at work, and so you won't get alot of attention til everyone gets home. Please don't double post.would appriciate any thoughts on this as i am hoping for a solution i located a main breaker but i dont want to mess with live current
Turn the main off and on...maybe a couple times. Turn all other breakers off first. Breaker need to be replaced at some point. It may be dead already.To help you understand, you have two hot legs @1 120 vots each, 240 volts between them. You have a bad connection somewhere in one of them. It could be the wires, the breaker or the internal compnents of the panel like the lugs or bus bar. The "silver" wire is the neutral/ground.
I don't say this very often, but:me too power went off again -i tryed turning off the breakers and resetting -no luck can someone tell me how dangerous this can get to leave it like this?