I'm replacing two outlets in my kitchen and have been confounded by what seems like a simple task. One of the outlets has 3 romax lines in it -- one hot and the other that feed other outlets in the kitchen. I'm assuming that the other outlet is being fed by this one, since it has a single romax line in it. Today I wired up a new outlet to the one with the 3 lines. I put the hot line in the top receptacle -- black to gold and white to silver. No problem, and the outlet has power. But, as soon as I add the other two lines it trips the breaker. I can't figure it out. Any ideas?