What precisilly is your problem ?I have found 6 receptacles on the same circuit, all of them open ground. I have rechecked the grounds and commons in the main panel, and actually tightened all of them again. Didn't find anything amis at the main box. Two of the recep boxes did not have grounds, so I fixed them, and actually replaced all 6 receptacles. Still have the issue. I checked every switch that we have and nothing appears to be on that circuit. It is all receptacles so far. Is that normal? I even checked all of the motion sensor lights , and nothing included in my circuit.
Any ideas out there? Even though the breaker has not tripped - could it have gone bad?
Could any other circuit be involved?
Is it just no ground ?
If it is, then the breaker would have no effect,
on an open ground situation !
Do you have hot and neutral at the recepticals ?
Are all these recepticals on one power circuit ?
And do you have earth continuity thru all these outlets ?
Do you know which is first in the power chain ?