Need some guidance that I can't find a real answer to. Recently (started late 2017) heavily remodeled our home and it now includes 2 separate laundry areas that were known to all to be equipped with high efficiency washers and gas dryers. No provision for electric dryers was to be installed. All electrical is new and installed by a licensed electrician and inspected as required. The burning problem is that each area was only equipped with one dedicated 15 amp duplex outlet. This does not sit right with me. If the electrician knew, should the areas not be serviced with a 20 amp circuit? Is this even enough?Should this have passed inspection in Ontario? Gas dryer manual says plug into a 15 amp circuit. Washer only says a protected outlet. The main section of the home's laundry room set-up was/is very obvious. 14/2 is all that runs to both. Nervous now that a tough re-wire has to be implemented to the main area. The other, well easier, will not be simple. Not bashing, but this particular individual will never be employed by me or any agents I use ever again.