I removed the cover of a 2 gang electrical box to replace some switches. The metal box inside is a 2 gang box, but it seems to have an extra pair of mounting tabs.
Most of the 2G metal junction boxes have mounting tabs at opposite corners to mount mud rings. 2G switch boxes have two pairs along two edges for direct mounting of switches or receptacles. Yet this box has two tabs at the corners, and next to those each tab there is an additional tab.
Here is a picture of the box.
As you can see, there is a flat 2G mud ring over it, secured by screws into the corner tabs. The last picture shows that clearly.
Yet there is an additional tab below the upper right corner, and above the lower left corner. What are those for?
With those tabs in the way, I cannot use a bulkier dimmer switch.
I'd apply some Dumore or other hand grinder to it. I can't say I've ever seen anything like that so perhaps someone got a little too creative. Replacing it will be advised if you can't grind the obstructions away and still have a safe switch box.
This is an older thread, you may not receive a response, and could
be reviving an old thread. Please consider creating a new thread.
DIY Home Improvement Forum
A forum community dedicated to Do it yourself-ers and home improvement enthusiasts. Come join the discussion about tools, projects, builds, styles, scales, reviews, accessories, classifieds, and more! Helping You to Do It Yourself!