fuse may be on your control board?? 3 or 5 amp? What do you think caused the problem?? secondary voltage is 24 VAC - read more post on this site -- pics??
That 3 amp fuse protects the 24VAC side- T/S wires //// check for a bare wire where the wires go into the furnace/ short to ground/ metal cabnet. Best of luck!!Found my 3a fuse on furnace board was shot. Replaced it. So far so good
Obviously, if it goes again, I will get service.
As far as what caused it to go bad, no idea. I didn't touch anything prior to noticing no heat. Thanks for your help.