Not all appliances are a continuous load. In residential the WH is about the only one; electric cook top and oven are not.
I would not install a sub unless you are short on breaker spaces. Run 10/2 for the WH, run 10/3 for the cook top, Run 10/3 for the oven. You could use 12/3 for the oven but 10/3 will future proof the install.
1 - 3 of 3 Posts
This is an older thread, you may not receive a response, and could be reviving an old thread. Please consider creating a new thread.
A forum community dedicated to Do it yourself-ers and home improvement enthusiasts. Come join the discussion about tools, projects, builds, styles, scales, reviews, accessories, classifieds, and more! Helping You to Do It Yourself!