math behind reducing main trunk size over lenght

14012 Views 3 Replies 4 Participants Last post by  beenthere
I'm just doing some of this in my head and was wondering about how you calculate the reduction of side in a main trunk duct as it gets longer..

does it have to do with the number of takeoffs over the length, or is it just length based?

It seemed like as you take air away you'd want it to get smaller to keep the velocity the same as the amount of CFM would reduce as you add more take offs... is this how it works?

never looked into this, tried to look it up on google, but haven't found much good info
1 - 1 of 4 Posts
Many reducing trunk systems really don't need to be reduced at all, since they are short, less then 24 linear foot.

As one poster stated, there are calculations done based on how many CFM will be moved through the next duct. These calcs are from manual D. Manual D is what you would use to determine what friction rate to use to size the trunk and supply lines. Using an arbitrary friction rate is asking for a bad duct design, and air flow problems.

You might want to get a copy of Manual D, and go through it. You will be surprised when you find out that there is virtually no such thing as a less then 100 foot total equivalent length duct system. And .1" friction rate is virtually never the correct friction rate to use. You'll also learn that friction rate and static pressure are not the same thing. Even though hordes of installers think it is.
1 - 1 of 4 Posts