Ground wires should go only to the ground bar,Do you see the clear jacket wire connecting neutral and ground bus bar,
Is this allowed ?
This is the only sub panel after the 100amp service disconnect , the report says the ground cannot be seen where the 100 amp box is. I am pretty sure that is grounded in some way to the meter or something
So then the ground and neutral wires can go into any of the terminals on either bus bar?
Neutral wires should only go to tne neutral bar.
The wire between the two is called the "BOND".
There should be only one of these, in the main panel.
if it is a sub panel there should not be one !