+I don't allow it. I was just adding a circuit for a basement receptacle. It is possible, when this was installed, the inspector let it ride.
Thanks, I didn't think so. If I tried something like that on commercial work, they'd change my pay grade.Should not have been allowed if inspected. Cables should have been clamped to panel in knockout.