GFCI will be provided upstream before it exits the nearby building. Yes, WR recepts are the plan. Thanks.WillK said:Assuming you're on 2008 NEC, your receptacles will need to be weather-resistant. These will have a WR on them. This includes the first one which must be a WR GFCI.
If not yet on 2008, the GFCI is still required. And I'm pretty sure the in-use weather cover is required by any code edition as well.