Discussion Starter · #1 ·
I have a 80% Goodman furnace that won’t start. The inducer turns on then it shuts down because the pressure valve won’t close. If I suck on the tube I can get it to fire and start. Exhaust pipe clear.port for tubing clear. Do I have a bad pressure switch?