Discussion Starter · #1 ·
I have a tub with jets in master bath, and there is a blank GFCI on the wall next to toilet. The wife hates this GFCI for aesthetic reasons. Was thinking about just removing the GFCI from there and installing GFCI breaker in basement. I've read about this and see that neutral needs to connect to breaker. There are several neutrals that feed the same conduit as the tub hot wire in panel. Questions; is neutral always run in same conduit with the hot wire? If so, what is the best way to identify the tub neutral when there is more than one in conduit?