This is an awesome idea, cant believe i didnt think about it. Especially because its 70kbtus, and i only need about 40kbtus, i bought this furnace in a pinch knowing it was wayyyy oversized, but basically this will put it at 35kbtus. which is fine. awesome, i cant see any damage being done by running it this way either. THANK ALL OF YOU FOR THE GREAT REPLIES IN A TIMELY FASHION. Ive been sitting here stressed out all day about it. You guys are great, im glad i made it here!!!!If it has two 60 amp breakers, turn one of them off. If the fan runs, the 60 in the panel will hold, but you'll get half of the heat.
If the fan doesn't run, turn that one back on and the other one off.
Most likely, one of the 60s has 10KW heat, the fan and the controls. The other 60 has only the remaining 10 KW heat.
This will get you by until it can be connected correctly.