I had to move a washer and dryer to a different place in our utility room which is a lot further from our breaker panel. We have another panel outside the house where the service entrance is and that has 8 spots for breakers as well. This outside panel is on the opposite side of the wall where the washer and dryer will be so it is much easier to move the breakers to this panel and wire it up that way. When we opened the panel we noticed it has a neutral bar but no ground bar. I can see the bare ground wire running through and above the 150 amp breaker and meter. For these two circuits, what should I do for the ground? Should I just clamp them to the ground wire? This isn't a problem in the other panel since it has the ground bar.