Check for power at the load side of the breaker,
Could be a faulty breaker.
If there is power on one side of the breaker, (supply side).
But no power on the load side, then it has tripped,
or it is faulty.
1 - 4 of 4 Posts
This is an older thread, you may not receive a response, and could
be reviving an old thread. Please consider creating a new thread.
A forum community dedicated to Do it yourself-ers and home improvement enthusiasts. Come join the discussion about tools, projects, builds, styles, scales, reviews, accessories, classifieds, and more! Helping You to Do It Yourself!