First time poster and wanted to extend a huge thanks for the wealth of information.
I have a detached garage 8-10 feet from the house. I brought a 20 amp circuit for outlets and 15 amp circuit for lighting to the garage from the house panel. By code I need to have a disconnect where the circuits enter the garage. I'm wondering if a 20 amp dual pole switch will suffice or do I need to install a larger 30 amp disconnect?
This is an older thread, you may not receive a response, and could
be reviving an old thread. Please consider creating a new thread.
DIY Home Improvement Forum
A forum community dedicated to Do it yourself-ers and home improvement enthusiasts. Come join the discussion about tools, projects, builds, styles, scales, reviews, accessories, classifieds, and more! Helping You to Do It Yourself!