Just had my dayton 3E369b 100,000 BTU heater installed and working in my garage. Moved it over 6" for better clearence of the joyces to install the vent pipe. Now it wont ignight...How do I purge the auto pilot valve?
Also my fan comes on in 20 seconds after thermostate is turned on weather the unit is lit or not. This is a brand new limit switch, did i wire it wrong. I don't have and can't find a Manual for this unit...
I have white on bottom right and the rest are blue wires. Checked and purged the gas at the valve. Does anyone have a better diagram or knowledge of how the wires go on the switch. I havent changed anything since it worked other than a 6" zip code. Is there an idiots guide to proccess of elimination...
Thanks in advance.
I have no spark. plus no sound or smell of gas. Just got a manual from Grainger for my 3e369b model, and am tiring to diagnose it today. Seen a Blocked Vent Switch on the wiring diagram...what sets this off.
This is an older thread, you may not receive a response, and could
be reviving an old thread. Please consider creating a new thread.
DIY Home Improvement Forum
A forum community dedicated to Do it yourself-ers and home improvement enthusiasts. Come join the discussion about tools, projects, builds, styles, scales, reviews, accessories, classifieds, and more! Helping You to Do It Yourself!