i as working on this package unit the one that come with the evaporator and condenser al together i have never worked on one the tech said the condenser motor was bad and the capacitor so i went ahead and replaced the motor and capacitor conected the two brown and brwon with white to the capacitor then conected the yellow to the yellow and the black to hat seems to be the red that cnnets into the black contactor i dint know what to do with hte ground wire on the motor ..and i turn the ac on and the motor doesnt run or start at all...if you need more details let me know
White is probably the common. And the motor is probably a 2 speed. And only the black, or red is connected, depending on what speed you want it to run at. Not both the black and red. Motor may be damaged now though.
This is an older thread, you may not receive a response, and could
be reviving an old thread. Please consider creating a new thread.
DIY Home Improvement Forum
A forum community dedicated to Do it yourself-ers and home improvement enthusiasts. Come join the discussion about tools, projects, builds, styles, scales, reviews, accessories, classifieds, and more! Helping You to Do It Yourself!