if a breaker tripped it needs to be turned completely to the off position and then back on for it to reset. if it isnt the breaker then might be a burned wire in one of the boxes since more then one light are on the same circuit.
1 - 1 of 1 Posts
This is an older thread, you may not receive a response, and could be reviving an old thread. Please consider creating a new thread.
A forum community dedicated to Do it yourself-ers and home improvement enthusiasts. Come join the discussion about tools, projects, builds, styles, scales, reviews, accessories, classifieds, and more! Helping You to Do It Yourself!