Ok..I've gone down a rabbit hole. I'm trying to find the minimum bend radius to pull service conductors, specifically 350-350-4/0 underground triplex with outer diameter of 1795 mils. Is the applicable code 338.24? And is it 5 times the cable diameter? So would it be ~9" min bend radius? Thanks!