Looking for some advice on electrical wiring. I hit a stump and not sure which way to go. Pictured below is a light box. The left is the hot that comes from the bathroom. The middle is for this room. And to the right is the closet light. When I arrived all blacks were tied together. And the two whites from the closet and bathroom were tied together. The solo white was for this room. So I hooked up the light in this room and it doesn't work. I check the voltage and there isn't any. So I separate the blacks. With all separate I only have voltage on the bathroom wires. If I tie the bathroom and this room together I get lights in this room and bathroom. But closet doesn't work. If I tie bathroom and closer together. I now have working closet lights and bathroom. But this room doesn't work. And with all three tied together, this room still doesn't work. Not sure exactly which direction to look at. Any help would be greatly appreciated.
18.7 KB Views: 69