My lights in the bathroom are on a 15A (14 gauge) circuit.
I only have 1 receptacle (GFCI) in this small bathroom that is 20A (12 gauge). I currently have this circuit wired to start at the bathroom GFCI receptacle and then it goes to the wet bar 20A receptacles (2 of them).
Is this allowed to have the bathroom and other two receptacles on the same circuit? I live in Kansas and couldn't find anything in the 2017 NEC that specifically called it out.
If it's not i'll just add another 20A breaker and run wire to the wet-bar receptacles, but was hoping I didn't need to.
This is an older thread, you may not receive a response, and could
be reviving an old thread. Please consider creating a new thread.
DIY Home Improvement Forum
A forum community dedicated to Do it yourself-ers and home improvement enthusiasts. Come join the discussion about tools, projects, builds, styles, scales, reviews, accessories, classifieds, and more! Helping You to Do It Yourself!