Discussion Starter · #1 ·
I have a 50 amp GFCI breaker in my main panel. this is for a sub panel in our backyard that has nothing connect to it currently. When I flip the breaker on it trips. I verified there was no continuity between the two black power wires. I disconnected those from the breaker And so the only thing connected to the breaker at the main panel is the neutral wire and the pigtail that goes to ground. When I turn the breaker on it still trips. Is this breaker bad?
1.5 MB Views: 143