I have a 3-way switch next to a single pole. Each control 4 cans in my basement (65 Watts each, Halogen). I put in a 3-way dimmer and a single-pole dimmer (both 600 W rated rated Lutrons). It's the first stage of the 3-way so I'm good there. I got all the wiring correct, doing it the same as in the regulars. I switched the 2 carry wires on the 3 way to check it out and makes sure I had it right. On both dimmers ... the dimming function doesn't work? The switches all otherwise work correct. Any ideas on what the could be going on? I'm anxious to get these recessed cans dimmable. Thanks!