Joe Willie· Registered
Discussion Starter · #1 ·
In a recent post I learned you could not use a tandem 20A breaker for 10-3 UF because the one neutral wire would be overloaded. I am confused about this. They said the problem would be eliminated if I used 2 single 20A breakers which would split the hots over 2 seperate poles. I understand that part but there still is just one neutral wire. Would I pigtail this to two seperate neutral bars? Please help me understand the what to do and why of this issue at the 200A house panel and the small panel I will use at the shed. Thank you.