We have a 20 amp dedicated circuit upstairs that only serves a small A/C unit (4.2 amps) and is really overkill. The cable is in a perfect location for me to tap into for an outside motion light and switch. I really prefer using #14 cable for several reasons.
Is it OK to splice into this #12 cable provided of course I switch out the breaker to a 15 amp breaker?
This is an older thread, you may not receive a response, and could
be reviving an old thread. Please consider creating a new thread.
DIY Home Improvement Forum
A forum community dedicated to Do it yourself-ers and home improvement enthusiasts. Come join the discussion about tools, projects, builds, styles, scales, reviews, accessories, classifieds, and more! Helping You to Do It Yourself!