I’m looking to add a new circuit to my electrical panel. There is plenty of space for the new breaker, but the neutral / ground bar is totally full. That’s not a big deal for the ground wire as you can have more than one ground wire to a screw. But it is a problem for the neutral as you are...
Here is a picture of both units.
If anyone can help me,im just not sure where to connect blue on the new unit. Also, do i need the jumper between w and y on the new like that?