I have a GFCI that wont reset. I did the following.
1. Replaced it, but still trips
2. Removed the load receptacles, but still trips
3. Checked voltage from hot to neutral. 118
4. checked Voltage from hot to ground. 118
5 turned circuit off at breaker box and check for continuity.