Photo of panel to be linked below as a reply.
I have taken on the task to wire a new 100AMP main electrical panel.
Have the permits from ESA. Want to make sure it's top shape.
Change out is from an old 100AMP Fuse box.
I have the two main legs feeding into the 100AMP breaker...
I want phone service installed in my new home. According to the phone company, I am required to provide a ground at the phone junction box. NEC 800.100 supports this assertion.
Unfortunately, it would be very difficult to run wire from the location of the phone junction box to the service...