Does anyone know an easy way to eliminate double tapped breakers? Ge does not seem to make a single pole Tandem breaker for this series of 100 amp panels? the slim line breakers do not fit. The only other options are to install a sub panel next to the main panel or use a pigtail, is a pigtail up to code inside the main panel? ?
Any all help would be greatly appreciated?
Re: Double taps in a GE power mark gold load center
QLine 1/2" breakers in 15 amp should fit, but only in certain places. I believe the top two spaces are not good for that. Pigtails are perfectly fine if the total amperage draw won't exceed the breaker capacity and the wire is of proper size.
Half of Communications is Listening, and You can't Listen with your Mouth.