my house is almost 3 years old. i have not had this problem until three weeks ago. the humidity level is at 88%. i can cool the house down and bring the humidity down some, but it will rise again as soon as i turn the a/c up.
Last edited by mfinley; 06-23-2010 at 04:12 PM.
Reason: i need this to be moved to hvac
this should be in the hvac forum. check your a/c condensate pan/drain (attic, basement or closet), make sure there is no standing water in the pan from a clogged or partially clogged drain. make sure there is good airflow over the coil, could be a dirty coil or a dirty air filter. could also be the coil freezing over due to low airflow and/or low system charge.
Last edited by NitroNate; 06-22-2010 at 04:05 PM.
The Following User Says Thank You to NitroNate For This Useful Post: