Voltage Drop ? - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Voltage Drop ?

 Thread Tools Tweet Share Display Modes
12-31-2010, 11:26 AM   #1
Newbie

Join Date: Dec 2010
Posts: 1
Rewards Points: 10

## Voltage Drop ?

I've installed a floodlight out in my yard 250 ft. from the house. I want to switch it from either the pole or the house and I want an outlet which is always hot at the pole. I like the "coast 3-way" wiring scheme since it will save me an extra 250 ft. conductor for the outlet. My concern is that with certain switch combinations it appears that the hot leg to the lamp could be 750 ft. in length. The light is metal halide pulse start with the ballast rated at 120V and 2.5 amps. Are there any potential light or light fixture performance issues ?

 12-31-2010, 11:40 AM #2 Member   Join Date: Nov 2007 Location: Nashua, NH, USA Posts: 8,597 Rewards Points: 2,800 What is a coast 3 way wiring scheme? You would not need a 750 foot current path. You need 4 wires from the house to the pole to have 3 way switching of the light and a receptacle that is always live. You need 3 wires from the house to the pole where the 3 way switching controls both the receptacle and the light at all times. You need just 2 wires from house to pole where you have a master switch for both light and receptacle at the house and optionally a slave switch that turns the light off at the pole. To run a reasonably heavy load appliance such as a hedge trimmer, you should use 10 guage wire. For only occasional and small current usage (about 7 amps including the light) you can get away with 12 gauge wire. For a 15 amp circuit you could run a 14-2 cable for the light 3 way part and a 10-2 for the receptacle and shared neutral. 10 gauge wire: 0.00118 ohms per foot. 12 gauge wire: 0.00187 ohms per foot. The number of volts dropped within the wires from your 120 volts (same number from a 240 volt circuit) equals the number of amperes being drawn times the resistance (in ohms) of the circuit round trip. __________________ Stick to your lawn watering schedule until it really starts to pour. After the storm you have only the same number of rest days you always had and then you need to start watering again. Last edited by AllanJ; 12-31-2010 at 12:05 PM.

 12-31-2010, 11:55 AM #3 Member   Join Date: Jun 2007 Posts: 4,109 Rewards Points: 308 Here is an interactive drawing of a California three way switch diagram. I am not certain it's legal as you are switching the neutral. If thats the case (non-compliant) it would be a waste of time to pull wires for it. I think at one time cal 3 ways were allowed and we sometimes run across one that makes for difficulty figuring out until you understand what you have. I personally would never use a cal 3 way method. Attached Images

12-31-2010, 11:57 AM   #4
Member

Join Date: Aug 2010
Posts: 480
Rewards Points: 330

Quote:
 Originally Posted by AllanJ What is a coast 3 way wiring scheme? You would not need a 750 foot current path. You need 4 wires from the house to the pole to have 3 way switching of the light and a receptacle that is always live. You need 3 wires from the house to the pole where the 3 way switching controls both the receptacle and the light at all times. You need just 2 wires from house to pole where you have a master switch for both light and receptacle at the house and optionally a slave switch that turns the light off at the pole.
for a lite with 3-way and always hot outlet,you need 5 wires.1 neutral,3 hot,one ground.with #10 wire drawing 10 amps you would be at 6 volt drop.if you use a multi-wire ckt and keep load down on the outlet #10 will get you by.

Last edited by oleguy74; 12-31-2010 at 12:04 PM.

 12-31-2010, 12:04 PM #5 Member   Join Date: Nov 2007 Location: Nashua, NH, USA Posts: 8,597 Rewards Points: 2,800 Oops, I did not count the bare wire as one. __________________ Stick to your lawn watering schedule until it really starts to pour. After the storm you have only the same number of rest days you always had and then you need to start watering again.
12-31-2010, 12:07 PM   #6
Member

Join Date: Aug 2010
Posts: 480
Rewards Points: 330

Quote:
 Originally Posted by J. V. Here is an interactive drawing of a California three way switch diagram. I am not certain it's legal as you are switching the neutral. If thats the case (non-compliant) it would be a waste of time to pull wires for it. I think at one time cal 3 ways were allowed and we sometimes run across one that makes for difficulty figuring out until you understand what you have. I personally would never use a cal 3 way method.
not legal beacause you canot switch a neutral.

12-31-2010, 12:11 PM   #7
Electrical Contractor

Join Date: Jun 2004
Location: Newnan GA
Posts: 8,150
Rewards Points: 946

Quote:
 Originally Posted by oleguy74 not legal beacause you canot switch a neutral.
Agreed!
__________________
Yes I am a pirate, two hundred years too late
The cannons don't thunder, there's nothing to plunder
I'm an over-forty victim of fate.

12-31-2010, 12:51 PM   #8

Join Date: Feb 2004
Location: NY State
Posts: 7,828
Rewards Points: 2,006

Quote:
 Originally Posted by jackscanlon I like the "coast 3-way" wiring scheme since it will save me an extra 250 ft. conductor for the outlet.
And other than here no one has told you how <not smart> and unsafe this is??? All to save \$20 worth of wire?

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post Moose50000 Electrical 2 02-28-2010 06:23 PM naehring2000 Electrical 5 02-10-2010 11:14 AM rnice Electrical 8 12-13-2009 08:43 PM rgsgww Electrical 12 12-09-2008 05:21 PM sushiboy Electrical 12 04-03-2008 09:01 PM

Top of Page | View New Posts