Ran A Wire To An Electrical Panel For My First Time - Electrical - Page 2 - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Ran a wire to an electrical panel for my first time

 Thread Tools Tweet Share Display Modes
07-19-2009, 08:20 PM   #16
Member

Join Date: Jul 2008
Location: NW of D.C.
Posts: 5,990
Rewards Points: 2,000

Quote:
 Originally Posted by darren Okay what are you talking about, i have never heard of this before.
That's 'cause it's original, sort of.
It's a more refined version of putting a 100w incand. lamp across an open breaker to check new work for shorts. The problem with incand. lamps is that the filament resistance depends on the current through it.
I carry a 100W, 100Ω rheostat that I got at a Hamfest to do these kinds of checks.

Series circuit consisting of 120v source, hair dryer, unknown load.

120/10A = 12Ω hair dryer ohms

120v/15A = 8Ω. load resistance for 15A
120 [8/(8+12)] = 48v across the load.
120-48 = 72v across the dryer. More than 72v is more than a 15A load.

Similarly for a 120v/20A = 6 Ω load (80v across the dryer) and for a 120/200 = 0.6 Ω load (114v across the dryer).

If the hair dryer fan actually runs at these low voltages you can leave it in the circuit for more than one or two seconds.

Last edited by Yoyizit; 07-19-2009 at 09:01 PM.

 07-19-2009, 09:15 PM #17 Electrician   Join Date: Nov 2005 Location: Winnipeg, Manitoba Posts: 1,381 Rewards Points: 968 Wow way to complicated for me, i will stick with turning the breaker on and seeing if it pops.

07-19-2009, 10:09 PM   #18
Wire Chewer

Join Date: Jun 2009
Posts: 3,550
Rewards Points: 528

Quote:
 Originally Posted by darren Wow way to complicated for me, i will stick with turning the breaker on and seeing if it pops.
That's my current method too lol. Though normally I'm 99% confident everything is ok. If I'm doing something more complicated I will find myself going back and forth often during the work to turn it on/off while testing wires that are not yet connected. I also often put two wires together (with no power) then test voltage at another end to see if it reads close to 0 then test for closed circuit using the feature on my multimeter, then I know where those two wires go. I found myself tracing stuff this way for a few hours when I found some weird setup in a junction box. Turns out the circuit that powers the lights in my crawlspace also powers the fridge.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post criehl Electrical 17 05-14-2009 08:05 AM 4x15mph Electrical 8 11-24-2008 01:00 PM Alan Electrical 10 04-12-2008 10:50 AM leonard_voet Electrical 19 04-09-2008 10:27 AM

Top of Page | View New Posts