Heat Pump Install Wiring Question - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum heat pump install wiring question
 User Name Remember Me? Password
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read Advertise About Us

 Thread Tools Tweet Share Display Modes
08-02-2009, 11:58 PM   #1

Join Date: Aug 2009
Posts: 1
Rewards Points: 10

## heat pump install wiring question

Hi All,

I am required to supply pig tails for my new heat pump and air handler/heat strips. I have done all the wiring in my home, but this one is perplexing.

The length of the wire run from the box is about 70' to the air handler with the 15kw heat strips. The heat pump is about 70' also.

The heat pump calls for a minimum branch circuit ampacity of 28 amps, but minimum circuit breaker protection rating of 40 and a max brkr of 45 amps.

The air handler/heat strips requires 2 circuits with one providing power to the air handler itself. It lists a heater amps per circuit of 40/24. So, it calls for minimum circuit ampacity of 55/30 with a maximum overload protection of 60/30.

So, I am trying to figure out what the minimum gage wire for each of the three circuits. It is all inside my residence. Also, what size breakers should I install?

Thanks alot for you knowledge.

 08-03-2009, 12:12 AM #2 Member   Join Date: Feb 2008 Location: Atlanta, Ga/Hamilton, Al Posts: 2,487 Rewards Points: 2,350 If you are using nonmetallic type cable, i.e. "romex", then you have all the info you need. For the heat pump, the min. circuit ampacity is 28 A, so you need a wire capable of carrying at least that. 10-2 is sufficient. A max circuit size of 45 A means you can use a breaker large as 45 A, but no less than 40 A. Since this is a residence, I'd probably use 8-2 with a 40 A breaker. On the air handler, it says you need two circuits, one capable of carrying at least 55 A, and another of at least 30 A. So, 6-2 and 10-2 respectively. Breaker sizes are 60 A (because there are no 55 A breakers available) and 30 A. Don't for get to provide a disconnect for all your circuits local to the equipment.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post tbrubes HVAC 7 02-04-2009 03:05 PM brutis HVAC 6 11-03-2008 10:06 AM Tom Williams HVAC 7 09-14-2008 07:40 AM thehotrod11 HVAC 3 12-29-2007 02:11 PM

Top of Page | View New Posts