Hallway Two Way Switches - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Hallway two way switches

 Thread Tools Tweet Share Display Modes
11-15-2010, 02:34 PM   #1
Member

Join Date: Aug 2009
Posts: 40
Rewards Points: 25

## Hallway two way switches

Hi: I have an hallway light fixtures which have a two ways switches(I beleive) you can control the fixture from begiining of hallway of a bedroom area and at end of the hallway .
How can you check and see which switch is out?

 11-15-2010, 02:40 PM #2 Licensed electrician   Join Date: Sep 2007 Location: Maryland Posts: 12,405 Rewards Points: 3,654 The proper terminology would be called a 3 way switch. What do you mean the switch is out? __________________ Answers based on the National Electrical Code. Local amendments may apply. Check with your local building officials.

 11-15-2010, 05:24 PM #3 Member   Join Date: Nov 2007 Location: Nashua, NH, USA Posts: 8,597 Rewards Points: 2,800 1. Find where the power comes in. The power feed wire is connected to the common terminal of one of the switches. Using a voltmeter you will always measure about 120 volts from that terminal to GROUND. 2. As you flip that switch you should measure 120 volts from just one of the other terminals and the 120 volts or nothing changes back and forth between those terminals (traveler terminals). 3. Now go to the second switch and measure between a traveler terminal and GROUND. As you flip the FIRST switch you should measure the 120 volts from one or the other traveler terminal of the second switch. 4. Measure between the common terminal and ground for the second switch. Depending on which traveler terminal of the SECOND switch has the 120 volts, the position of the second switch should put the 120 volts at the common terminal. If 1 fails you have a power problem as opposed to a switch problem. If 2 fails then the first switch is bad. If 3 fails then there is a bad connection between the two switches. If 4 fails then the second switch is bad. __________________ Stick to your lawn watering schedule until it really starts to pour. After the storm you have only the same number of rest days you always had and then you need to start watering again.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post curious1 Electrical 1 10-26-2010 10:26 PM DangerMouse Electrical 24 07-23-2010 04:13 PM Abs777 Electrical 6 04-28-2010 10:09 AM RyanD Electrical 19 05-26-2009 06:19 PM magnolia Electrical 3 05-09-2008 09:40 PM

Top of Page | View New Posts