Got the job done, after tearing out a few more holes Finally got to trace out each cable. Was a tricky one, The jobs was in a mini mall, and of course there was no one panel per store. Due to stores coming and going and/or expanding by taking over space next door there could be several stores pwr shut off's on one panel. Could not do job after stores hrs and disconnect pwr due to the fact there could be security line tied in to a breaker I need to turn off.And During stores hrs there were breakers with cashes and pc on it. Bet they love to get half way thru checking in and Power shut off..lol, After locating each line and the termination in panel. Shut one breaker off at a time and chk with storer to see what they lost, then rerouted pwr so they can continue business as I repaired the line. Had to do this for each of the 7 lines. Hr job took Several due to running aroung the dam mall.. lmao
Thanks for suggestions
By the Way DPPEW is short for DESPISE PIZZ POOR ELECTRICAL WORK, Take an extra second and DO IT RIGHT!!!
I wrote underline which you mention now but not before due in the minimall it is a commercal location and this really it must be done by legit electrician and have proper permit for it.
The minimall have alot of goofy set up with electrical system and belive or not it don't take much to get screw up.
I allready did see some of the store owner or GC's try to do the shortcut and the result is pretty messy if not done properly.